Fully automatic in operation and requiring no action LCP Control Panel is pneumatically operated by the service gas on pressure differential basis and needs no electrical supply to operate. It will continue to function therefore, should there be failure in electrical supply.
It is equipped with a shuttle valve and takes on automatically from empty cylinder bank to full cylinder bank.
The panel is enclosed in a metal cabinet with a hinged front cover. The cover is fitted with a lock to prevent unauthorized access, and can be swung open for maintenance.
A visual indication of the manifolds is provided by the three gauges within the control panel, clearly visible to through the transferred cover, these gauges indicates the pressure of right and left hand cylinder banks and the supply pressure from the control panel to the distribution system.
The panel is supplied with sensing facilities to provide visual signals and other ancillary services.
In addition the panel is fitted with audio alarm indication for change over from empty cylinder bank to filled cylinder bank.